__Three-phase to Two-phase Conversion and vice-versa__

__Three-phase to Two-phase Conversion and vice-versa__

This conversion is required to supply two-phase furnaces, to link two-phase circuit with 3-phase sys- tem and also to supply a 3-phase apparatus from a 2-phase supply source. For this purpose, Scott connection as shown in Fig. 33.17 is employed. This connection requires two transformers of different ratings although for interchangeability and provision of spares, both transformers may be identical but having suitable tappings.

If, in the secondaries of Fig. 33.14 (*b*), points *c *and *d *are connected as shown in Fig. 33.18 (*b*), then a 2-phase, 3-wire system is obtained. The voltage *E**d**c **i**s 86.6 V but *ECb = 100 V, hence the resulting 2-phase voltages will be unequal. However, as shown in Fig. 33.19 (*a*) if the 3-phase line is connected to point *A*1, such that *D**A*1 represents 86.6% of the teaser primary turns (which are the same as that of main primary), then this will increase the volts/turn in the ratio of 100 : 86.6, because now 86.6 volts are applied across 86.6 per cent of turns and not 100% turns. In other words, this will make volts/ turn the same both in primary of the teaser and that of the main transformer. If the secondaries of both the transformers have the same number of turns, then secondary voltage will be equal in magnitude as shown, thus resulting in a symmetrical 2-phase, 3-wire system.

Consider the same connection drawn slightly differently as in Fig. 33.20. The primary of the main transformer having *N*1 turns is connected between terminals *C**B *of a 3-phase supply. If supply line voltage is *V*, then obviously *V**A**B *= *V**B**C **= V**C**A *= *V *but voltage between *A *and *D *is *V *´ 3/ 2. As said

above, the number of turns between *A *and *D *should be also ( 3 / 2) *N*1 for making volt/turn the same in both primaries. If so, then for secondaries having equal turns, the secondary terminal voltages will be equal in magnitude although in phase quadrature.

Hence, the currents in the lines *B *and *C *are obtained vectorially as shown in Fig. 33.22. It should be noted that as the two halves of the teaser primary current flow in opposite directions from point *D*, they have no magnetic effect on the core and play no part at all in balancing the secondary ampere-turns of the main transformer.

The line currents thus have rectangular components of *K**I*2*M *and 0.58, *K**I*2*T *and, as shown in Fig. 33.22, are in phase with the primary star voltages *V**N**B *and *V**NC *and are equal to the teaser primary current. Hence, the three-phase side is balanced when the two-phase load of unity power factor is balanced.

Fig. 33.23 (*a*) illustrates the condition corresponding to a balanced two-phase load at a lagging power factor of 0.866. The construction is the same as in Fig. 33.22. It will be seen that the 3-phase side is again balanced. But under these conditions, the main transformer rating is 15% greater than that of the teaser, because its voltage is 15% greater although its current is the same.

###### Hence, we conclude that if the load is balanced on one side, it would always be balanced on the other side.

The conditions corresponding to an unbalanced two-phase load having different currents and power factors are shown in Fig. 33.23 (*b*). The geometrical construction is similar to those explained in Fig. 33.22 and (*a*).

**Summarizing the above we have :**

1.Teaser transformer primary has 3/ 2 times the turns of main primary. But volt/turn is the same. Their secondaries have the same turns which results in equal secondary terminal voltages.

2.If main primary hasN1 turns and main secondary hasN2 turns, then main transformation ratio is

3.If the load is balanced on one side, it is balanced on the other side as well.

4.Under balanced load conditions, main transformer rating is 15% greater than that of the teaser.

5.The currents in either of the two halves of main primary are the vector sum

**Example 33.18. ***T**wo transformers are required for a Scott connection operating from a 440-V, 3-phase supply for supplying two single-phase furnaces at 200 V on the two-phase side. If the total output is 150 kVA, calculate the secondary to primary turn ratio and the winding currents of each transformer.*

**Note****. **We have made use of the fact that since secondary load is balanced, primary load is also balanced. If necessary, *I*1*M *can also be found.

**Exampl****e 33.20. ***In a Scott-connection, calculate the values of line currents on the 3-phase side if the loads on the 2-phase side are 300 kW and 450 kW both at 100 V and 0.707 p.f. (lag) and the 3-phase line voltage is 3,300 V. The 300-kW load is on the leading phase on the 2-phase side. Neglect transformer losses. ***(Elect****. Technology, Allahabad Univ. 1991)**

**Solution****. **Connections are shown in Fig. 33.25 (*a*) and phasor diagram in Fig. 33.25 (*b*).

**Exampl****e 33.21. ***T**w**o electric furnaces are supplied with 1-phase current at 80 V from a 3-phase, 11,000 V system by means of two single-phase Scott-connected transformers with similar secondary windings. When the load on one furnace is 500 kW (teaser secondary) and on the other 800 kW (secondary of main transformer) what current will flow in each of the 3-phase lines (a) at unity power factor and (b) at 0.5 power factor ? Neglect phase displacement in and efficiency of, the transformers. ***(Electrica****l Engineering, Madras Univ. 1987)**

**Solution****. **The connections are shown in Fig. 33.26 and the phasor diagrams for unity and 0.5 p.f. are shown in Fig. 33.27 (*a*) and (*b*) respectively.

**Example 33.23. ***T**wo single-phase Scott-connected transformers supply a 3-phase four-wire distribution system with 231 volts between lines and the neutral. The h.v. windings are connected to a two-phase system with a phase voltage of 6,600 V. Determine the number of turns in each section of the h.v. and l.v. winding and the position of the neutral point if the induced voltage per turn is 8 volts.*

**Solution. **As the volt/turn is 8 and the h.v. side voltage is 6,600 V, the h.v. side turns are = 6,600/8 = **82****5 **on both transformers.

**Example 33.24. ***A Scott-connected (2 to 3-phase) transformer links a 6,000 V, 2-phase system with a 440 V; 3-phase system. The frequency is 50 Hz, the gross core area is 300 cm**2**, while the maximum flux density is to be about 1.2 Wb/m**2**. Find the number of turns on each winding and the point to be tapped for the neutral wire on the 3-phase side. If the load is balanced on the one side of such a transformer, find whether it will also be balanced on the other side. ***(Londo****n Univ.)**

**Solution. **Use the transformer voltage equation 1,

**Tutorial Problem No. 33.3**

**1. **A Scott-connected transformer is fed from a 6,600-V, 3-phase network and supplies two single-phase furnaces at 100 V. Calculate the line currents on the 3-phase side when the furnaces take 400 kW and 700 kW respectively at 0.8 power factor lagging. **(Elect. Machines II, Indore Univ. 1977)**

**[With 400 kW on teaser, line currents are 87. 2 A; 139 A; 139 A]**

**2. **Two 220-V, 1-phase electrical furnaces take loads of 350 kW and 500 kW respectively at a power factor of 0.8 lagging. The main supply is at 11-kV, 3-phase, 50 Hz. Calculate current in the 3-phase lines which energise a Scott-connected transformer combination. **(Elect. Machines, Madras Univ. 1978)**

**[With 350 kW on teaser line currents are : 45.7 A ; 61.2 A; 61.2 A]**

**3. **Two electric furnaces are supplied with 1-phase current at 80 V from 3-phase, 11,000-V supply mains by means of two Scott-connected transformers with similar secondary windings. Calculate the current flowing kW respectively in each of the 3-phase lines at U.P.P. when the loads on the two transformers are 550 kW of 800 kW.

**[****W****it****h 550 kW on teaser, line currents are : 57.5 A; 78.2; 78.2 A] (Electrical Machines-I, Madras ****University, 1977)**

#### Incoming search terms:

- scott connection 3 phase to 2 phase conversion
- 3 phase to 2 phase conversion
- three phase to two phase conversion
- 3 to 2 phase conversion
- is ir possible to change 3 phase to 2 phase with standard transformers
- three phase to two phase transformation
- 3 phase to 2 phase
- 3 phase to 2 phase transformation
- conversion of 3 phase to 2 phase
- 3phase to 2phase conversion
- 3 phase to 2 phase conversion methods
- how to convert 3 phase to 2 phase
- converting two phase to three video
- scott transformer example problems
- converter transformer 3 phase
- Polyphase transformers mail
- three phase to two phase converter
- to conversation in 3 phase to 2 phase
- [50 hz; 1530 v; 2650 v] (electrical machines-i indore univ april 1977)
- 3 phase to 2 phase transformer
- 3phase from d c current
- circuit diagram and phasor diagram showing how 2 phase supply can be obtained from a 3 phase supply
- how to convert three phase to two phase
- scott connection calculations
- three phase to two phase
- Two phase transformer
- 11000 to 440 transform image
- 2 phase system images
- 2 phase to 3 pjase covertikn aand vice vercaa
- 3 phase to 2 phase connection
- 3 phase to 2 phase conversion circuit diagram
- 3 phase to 2 phase conversion using scott connection
- 3 Phase to 2 Phase coversion using scott connectio
- 3 phase to 2 phase transformer conversation
- 3-phase to 2-phase conversion
- connectuons 3 phase to 2 phase conversion
- convert 3 phase to 2 phase power
- convert 3-phase to2-phase using single phase transformer circuit diagram
- convert three phase two phase
- converting 3 phase to 2 phase
- explain the scott connection of 3pase to 2phase conversion
- how convert three phase to two phase
- in scott connection is the 3-phase supply connected to 2-phase balanced?how?
- is it possible 3 phase ac supply from 2 phase supply using scott connection
- Is it possible to change a three phase transformer to two phase transformer
- is it there any method for conversion of 3ph to 2ph
- three phase to two phase conversion of transformer
- Three-Phase transformers
- Transformer calculation
- -30° lag phase displacement diagram in a 3phase transformer
- 100 kv3 fase transformer delta connection pics
- 11000 to 440 voltege digram
- 11000 volt transforma connection
- 2 electrical furnace are supplied with 1 phase current at 80 v from a secondary winding when the load on 1 furnace is 500kw & on other 800kw 2 of main transformer what current will flow in each the 3 phase line at o 5 power factor
- 2 ph to 3 ph conversion
- 2 PHASE EXTRUCTION
- 2 phase method in electrical
- 2 phase to 3 phase transformer
- 2 single phase transformers to 3 phase
- 2Ph to 3Ph transformer
- 2phase 3phase image
- 2phase consion
- 3 lives but two shorted on supply to form 2 phase system
- 3 phase convert to 2 phase system
- 3 phase current formula
- 3 phase to 2 ph conversion
- 3 phase to 2 phase conversion by using scott connection
- 3 phase to 2 phase conversion except
- 3 phase to 2 phase conversion in transformer
- 3 phase to 2 phase conversion of supply
- 3 phase to 2 phase conversion transformer pdf
- 3 phase to 2 phase conversion transformer with diagram
- 3 phase to 2 phase converted
- 3 phase to 2 phase convesion transformer
- 3 phase to 2 two phase conversion and vice versa
- 3 phase to 2phase conversion
- 3 phase transformers winding connection samples
- 3 phase transmission line voltage
- 3-2 phase conversion
- 3ph-2ph converting systems
- 3phase / two-phase transformer
- 3phase all conections image
- 3phase to
- 3phase to 2
- 3phase to 2 phase conversion of 3phase transformer
- 3phase to 2 phase in tr
- 3phase to 2ph conversion
- 3to 2 phade transformation
- 3to 2phase conversion of transformer application
- a 200 year old single phase furnace text alot of Shukla and secured respectively at a power factor of 0 707 lakh in and are supplied by 6600 fold three phase supply through Westcott connection calculate the current in 3 phase line neglecting losses
- a mathematical tool for 3 phase to 2 phase conver
- a mathematical tool of 3 phase to 2 phase conversion
- A three-phase transformer is made up of three identical single-phase transformers each specified by XLV =0 12 [Ω] and turns ratio NHV /NLV =30 Neglect resistances and magnetizing current The three-phase transformer steps up the voltage produced by a three
- application of 2 phase to 3 phase transformation required
- applications of 3 phase to 2 phase coversion
- applications of 3ph to 2ph scott connections
- calculate current in 3 phase lines which energize a scott connection transformer answer solution
- calculations for Scott connection
- can a 3phase transformer be changed to a twophase transformer? how??
- can we convert 2phase to 3 phase
- changing three phase to 2 phase transformer
- circuit diagram of 3phase to 2phase conversion by scott meter
- circuit diagram on conversion of 3phase transformer supply to 2 phase transformer supply
- condition for a transformer convert three phase to two phase
- Conversation 3 phase to 2 phase
- conversation of 3 phase transformer to 2 phase
- conversion from 3 phase to 2 phase
- conversion from 3phase to 2phase
- conversion from three phase to two phase
- conversion of 2phase transformer into 3phase transformer
- conversion of 3 phase to 2 phase system
- conversion of 3 phase to 2 phase using scott connection
- conversion of 3 phase transformer into two phase
- conversion of energy from 3 phase to 2 phase vice versa using single transformer
- conversion of three phase in two phase
- conversion of three phase to two phase
- conversion of three phase transformer to two phase transformer and vice versa
- conversion two phase to three phase from transformer
- convert 3 phase to 2 phase
- convert 3 phase transformer to two phase
- convert three phase supply to two phase
- converter three phase to twoe phase using single phase transformer
- convertion of 3phase to 2phase
- Coversion from 3 phase to 2 phase suppy
- Derivation For teaser transformer
- different 3 phase to 2 phase transformation
- different methods of conversion of 3 phase to 2 phase conversion
- different methods of phase conversion from three phase to two phase
- Discuss conversion from 3 phase to 2 phase using Scott connection
- discuss conversion from 3phase to 2phase using Scott connection answer this question
- equipment connected to 2phase
- Explain 3phase to 2phase conversion
- Explain How three phase to two phase conversion transformer
- explain in detail the conversion of three phase to two phase transformer
- explain scott connection for three phase supply
- explain scott connection with phasor diagram
- explain the conversion of 3-phase to 2-phase
- explain the conversion of 3-phase to 2-phase and vice-versa
- explain the method for 2 phase to 3 phase transformation
- explain the method of conversation of 3phase to 2phase
- explain three phase to two phase conversion with detail
- explain with diagram conversion of 3 phase to 2 phase transformers
- explain with the help of connection and phasor diagram how scott connection are used to obtain 2 phase supply for 3 phase supply mains
- from 3phase to connect 2 phase
- How 2 phase can be obtained from 3 phase without using scott connection?
- How 2 phase supply can be obtained from 3 phase
- how 3 phase is convert to 2 phase
- how can we convert 3ph supply to 2ph supply
- how change 3 phase to 2 phase
- how convert 3 phase to 2 phase??
- how convert 3ph to 2ph transformer
- how supply in phase to phade
- how to change three phase transformer to two phase
- how to connect 11000 volt to single phase
- how to connect three phase with two phase
- how to convert 3-phase to 2-phase
- how to convert 3phase into 2phase
- how to convert a 3faze to a 2 faze
- How to convert three phase in to two phase
- how to convert three phase transformer to two phase transformer and vice versa
- how to convert two phase to tvreephase
- how to devide kw between two phases
- how to obtain 2 phase from 3 phase
- how two three-phase transformers can be used to convert three-phase supply to a two-pjase supply
- how will you supply two single phase furnaces using scott connection
- in a scott connected transformer number of primary and teaser turns respectively are
- in autotransformer the power factor in coversion of two phase to three phase
- intercoversion of three phase to two phase
- Is it possible to change 3 phase to 2 phase or vice versa with standard transformer
- is it possible to change 3 phase to 2 phase transfermor
- Is it possible to change a 3 phase transformer into a 2 phase transformer?
- is it possible to change three phase to two phase
- Is it Possible to Change Three Phase to Two Phase or Vice-Versa with Standard Transformers?
- is it possible to change three phase to two phase with standard transformer
- is it possible to changr 3 phase to 2 phase in transformers
- is it possible to get balanced 3phase supply from 2 phase supply
- is there any other method for 3 phase to 2 phase connection
- is there any other method than scott connection
- methods for converting 3 phase to 2 phase current
- methods of 3 phase to 2 phase conversion method
- methods to convert 3 phase to 2 phase
- name a method of 3 phase to 1 phase conversion
- name method for 3 phase to 1 phase conversion and comment it
- name the connection which is used for conversion of three phase to two phase
- neutral current calculation formula in single phase
- notes transformer about phase conversation
- obtain 2phase supply from 3phase using scott connection
- output equation of single phase transformer
- Phase changer transformers
- phase conversion
- phase conversion in transformer 3 phase to 2 phase
- phase conversion ins transformers
- phase conversion of transformer
- phasor of scott connection
- picture of all part in distibution transformer upto 11000/440 volt
- picture of two phase wiring
- possible chandlge 3-phase to2phase or vice varsa with standard transformer
- problem on Scott connection
- problems on scott connection
- schematic diagrams of converting 3phae transformer wiring to 2phase and single phase
- scot conection or 2 phase to 3 phase conerter
- scot connection voltage equation of input output voltage equation?
- scott cnnection three phaae to two phase conversion short notes
- Scott connection 2 phase and 3 phase
- scott connection 3phase to 2phase transformer practical image
- scott connection cakculation
- Scott connection diagram
- scott connection for three phase to two phase conversion
- scott connection furnace numerical
- scott connection of a trandformer simple problems with solutions
- scott connection of transformer
- scott connection of transformer phasor diagram for leading
- scott connection or 3 phase to 2 phase conversion
- scott connection phasor diagram
- scott connection three phase to two phase conversion
- scott connection transformer images
- scott connection(3 phase to 2 phase conversion)
- scott three phase /two connection
- short note on three phase to two phase conversion
- similarities of alternator and two phase transformer
- single phase connection into 3 phase connection
- single phase supply conversation into three phase
- single phase to 2phase converd daigram
- single phase to three phase conversation equipment used
- single phase to two phase transformer diagram
- single phase transformer formula
- teaser transformer scott connection
- three phase chage to two phase
- three phase convert to two phase
- three phase convert two phase
- three phase to 2 pha
- three phase to 2 phase conversion and vice versa
- three phase to coordinate system
- three phase to two phase converdion
- three phase to two phase conversion (scott connection)
- three phase to two phase conversion in transformer
- three phase to two phase conversion of transformer pdf
- three phase to two phase conversion transformer
- three phase to two phase converter short note
- three phase to two phase Transformer
- three phase to two phase transformer schematic
- three phase two phase transformation
- three to two phase conversion of transformer
- three-phase to two-phase transformer
- three/two-phase conversion
- to obtain 3 phase to 2 phase conversion by scott connection
- to perform 3phase to 2 phase consversion
- tranfarmar exchang to 11000 to 440 volt daigram
- Transformation of 3phase into 2phase
- transformation of 3phase to 2phase
- transformator 2 phase to 3 phase
- transformer for 3phase to 2 phase
- transformer phase shift) Is it Possible to Change Three Phase to Two Phase or Vice-Versa with Standard Transformers?
- transformer supplier uae mail
- Transformers Converters
- two pahse to 3 phase transformer
- two phase fed from single phase supply
- two phase three phase line picture
- two Phase to three phase transformation
- two single phase transformer for conversion three phase into two phase
- vector conversion of three phase to two phase
- what is the formulae of scott conection transformer
- What is the ratio of number of turns on the primaries of teaser and main transformer?
- Where used star -delta transformer connection
- why 3 phase to 2 phase conversion
- why 3 phase to 2 phase transformation
- why transforming 3phase to 2phase
- with phasor diagram explain how 2 phase supply can be obtain from 3 phase
- write a short note three phase to two phase conversion
- www sample problem of three phase transformer images