1. Which of the following connections is best suited for 3-phase, 4-wire service ?
(a) ∆ − ∆ (b) Y − Y
(c) ∆ − Y (d) Y − ∆
2. In a three-phase Y-Y transformer connection, neutral is fundamental to the
(a) suppression of harmonics
(b) passage of unbalanced currents due to
(c) provision of dual electric service
(d) balancing of phase voltages with respect to line voltages.
3. As compared to ∆ − ∆ bank, the capacity of the V − V bank of transformers is ……… percent.
(a) 57.7 (b) 66.7
(c) 50 (d) 86.6
4. If three transformers in a ∆ − ∆ are delivering their rated load and one transformer is removed, then overload on each of the remaining transformers is ……… percent.
(a) 66.7 (b) 173.2
(c) 73.2 (d) 58
5. When a V − V system is converted into a ∆ − ∆ system, increase in capacity of the system is ……… percent.
(a) 86.6 (b) 66.7
(c) 73.2 (d) 50
6. For supplying a balanced 3 − φ load of 40-kVA, rating of each transformer in V − V bank should be nearly ……… kVA.
(a) 20 (b) 23
(c) 34.6 (d) 25
7. When a closed − ∆ bank is converted into an open − ∆ bank, each of the two remaining transformers supplies ……… percent of the original load.
(a) 66.7 (b) 57.7
(c) 50 (d) 73.2
8. If the load p.f. is 0.866, then the average p.f. of the V – V bank is
(a) 0.886 (b) 0.75
(c) 0.51 (d) 0.65
9. A T − T connection has higher ratio of utilization that a V − V connection only when
(a) identical transformers are used
(b) load power factor is leading
(c) load power factor is unity
(d) non-identical transformers are used.
10. The biggest advantage of T – T connection over the V – V connection for 3-phase power transformation is that it provides
(a) a set of balanced voltages under load
(b) a true 3-phase, 4-wire system
(c) a higher ratio of utilization
(d) more voltages.
11. Of the following statements concerning parallel operation of transformers, the one which is not correct is
(a) transformers must have equal voltage
(b) transformers must have same ratio of transformation
(c) transformers must be operated at the same
(d) transformers must have equal kVA ratings.
An auto-transformer is more efficient in transferring energy from primary to secondary circuit.
Because it does so both inductively and
(a) statement is false, reason is correct and
(b) statement is correct, reason is correct but
(c) both statement and reason are correct and
are connected to each other as cause and
(d) both statement and reason are false.
13. Out of the following given choices for poly phase transformer connections which one will you select for three-to-two phase conversion ?
(a) Scott (b) star/star
(c) double Scott (d) star/double-delta
14. A T − T transformer cannot be paralleled with …….. transformer.
(a) V − V (b) Y − ∆
(c) Y − Y (d) ∆ − ∆
15. Instrument transformers are used on a.c. circuits for extending the range of
(a) ammeters (b) voltmeters
(c) wattmeters (d) all of the above.
16. Before removing the ammeter from a current transformer, its secondary must be shortcircuited in order to avoid
(a) excessive heating of the core
(b) high secondary e.m.f.
(c) increase in iron losses
(d) all of the above
Incoming search terms:
- Copyright © www www examrace com If the load p f is 0 866 then the average p f the v-bank is Read more at: https://www examrace com/IES/IES-Practice-Questions/Electronics-Questions/Electronics-Engineering-Part-1 html Copyright © www www examrace com
- if the load p f is 0 866 then the avearage p f the V bank
- if the load power factor is 0 866 then the average power factor of V-V bank is
- which of the following statement concerning parallel operation of transformer is incorrect
- which of the following is best suited for 3phase -4wire
- When a V-V three phase transformer system is converted into a - system increase in capacity of the system is
- the folllowing statements about 3 phase transformer connection are all true except
- if the load power factor is 0 866 then the average power factor of the V bank is
- if the load pf is 886 then the average pf of the v bank is
- if the load pf is 0 886 then the average pf of the V-V bank is?
- If the load pf is 0 866 then the average pf of v - bank is 0 866;0 51;0 65;0 75
- if the load pf is 0 866 then the average p f the v-bank is what
- if the load p f is 866
- if load pf is o 866 then avarage pf od V-V bank is?
- if load pf is 866 then average p f is
- which one of the following is best suited for a 3phase 4 wire service